The parameterization of the HOOC Gateways (series H) from firmware 2.x.x can be done via browser.
The device obtains an IP address via DHCP in the factory settings. In addition, the HOOC Gateway is configured with a static IP address 172.17.17.17.
Follow the instructions below to connect (your PC) to the HOOC Gateway:
The configuration mode can be activated by pressing the reset button briefly (1 sec).
The configuration mode can be activated remotely with the HOOC App. The activation code of a HOOC Gateway can be generated either in the sites overview or in the menu “Secure Remote Access”.
The generated code can now be used to activate the configuration mode.
If the configuration mode is active, the power LED (red) lights up continuously.
The configuration mode can be deactivated by pressing the Leave configuration mode item, or it automatically dactivates 30 seconds after disconnecting from the configuration page.
If the configuration mode is inactive, the power LED flashes white.
Once the new settings have been made, they can be transferred to the HOOC Gateway by clicking on the Apply changes element.
The device obtains an IP address via DHCP. If required, this IP address can be defined statically.
The WiFi can be used as an access point for the LAN network. The password corresponds to the serial number of the gateway by default and is switched off.
The power supply of the USB interfaces is switched on at delivery.
HOOC offers the possibility of converting data from a KNX USB interface into data from a KNX IP gateway or KNX IP router. Thus a KNX USB interface can also be used as a “terminal device” in the Secure Remote Control service via HOOC Connect. The following settings can be made:
|KNX enabled||Enables/disables KNX functionality|
|Interface Name||Name of the interface (displayed in the ETS)|
|KNX Address||KNX source address of the HOOC Connect to be used|
|Client Addresses||KNX start source address to be used for packets and number of parallel connections for (KNX IP tunneling)|
The source addresses 1.1.240 to 1.1.249 are used for the setting 1.1.240 and 10 Client Address.
A commercially available KNX USB interface can be connected to USB port 1. The connection status of the KNX USB interface is displayed directly including information about the manufacturer and the model. The list below gives an overview of supported and ETS tested types.
|KNX USB Interface||USB Vendor ID||USB Product ID||tested (ETS)|
|Siemens KNX/EIB-USB Interface (Flush mounted)||0e77||0111|
|Siemens KNX/EIB-USB Interface (DIN rail)||0e77||0112|
|Siemens OCI700 Service Interface||0681||0014|
|Merlin Gerin KNX-USB Interface (Flush mounted)||0e77||0141|
|Hensel KNX-USB Interface (Rail mounted)||0e77||0121|
|Busch-Jaeger KNX-USB Interface (Flush mounted)||145C||1330|
|Busch-Jaeger KNX-USB Interface (surface mounted)||145C||1490|
|ABB STOTZ-KONTAKT KNX-USB Interface (MDRC)||147B||5120|
|Feller KNX-USB Data Interface||135E||0026|
|JUNG KNX-USB Data Interface||135E||0023|
|Gira KNX-USB Data Interface||135E||0022|
|Berker KNX-USB Data Interface||135E||0021|
|Insta KNX-USB Data Interface||135E||0020|
|Weinzierl KNX-USB Interface (Flush mounted)||0e77||0102|
|Weinzierl KNX-USB Interface (RS232)||0e77||0103|
|Weinzierl KNX-USB Interface (Rail mounted)||0e77||0104|
|Tapko USB Interface||16D0||0490|
|Hager KNX-USB Data Interface||135E||0025|
|Preussen Automation USB2KNX||16D0||0492|
|Merten KNX-USB Data Interface||135E||0024|
|b+b EIBWeiche USB||04cc||0301|
|Mean Well KSI-01U||28c2||0013|
|Apricum KNX USB Interface UIM||28c2||000f|
SERA can be activated or deactivated here.
Deactivating will prevent the HOOC Gateway to connect to the HOOC Cloud and the services of HOOC will no longer be usable.
When deactivating the setting “Allow enter config mode by pressing reset button”, the configuration mode cannot be more can be activated with the reset button (local). The activation of the configuration mode can only be done with an activation code take place. Thus, persons without access authorization to the site cannot reconfigure the device.
The advanced settings shows the device status and the device information.
The device can be rebooted by clicking on the Restart element without interrupting the power supply.
Clicking on the Reset element resets the device to the factory settings.
HOOC recommends regular updates of the firmware. The firmware can be downloaded from the HOOC Management Portal at the corresponding site under the menu HOOC Gateway -> Configuration.
Follow the instructions in the configuration tool and make sure that the power is not interrupted during the upgrade process!